Pellet Stove BURNiT Advant B2
от 2 989,00 лв.
Pellet Stove BURNiT Advant B2 is a convenient heating solution. Does not require a separate boiler room. Pellet stove is easy to install, space-saving, equipped with convenient electronic control. Simplicity and elegance for a living room, a restaurant or a hotel lobby. Heated and decorated room overlooking the living fire.
The combustion chamber of pellet stove is protected by large surface heat-exchanger (water jacket). It contributes to better efficiency of pellet stove.
The BURNiT Advant B2 model is designed without decorative glass, with additional insulation on the water jacket, which allows mounting on a balcony or in a closet. This saves space and maintains optimum efficiency.
Clean and fuel-saving combustion.
Contemporary design. Colors: Burgundy, Light Ivory, Jet Black.
Built-in pellet burner, fuel hopper, circulation pump and expansion vessel
The model is designed without decorative glass, with additional insulation on the water jacket, which allows mounting on a balcony or in a closet.
|Advant B2 13||Advant B2 18||Advant B2 25|
|Nominal Power||kW||13 kW||18 kW||25 kW|
|Heat power /reduced power/||kW||5,5 kW||7.1 kW||11 kW|
|Heat power Water mantle||kW||11||15.5||21.5|
|Width L/ Depth D||mm||530/520||530/520||600/580|
|Volume of water jacket||l||18||23||35|
|Expansion vessel volume||l||8||8||8|
|Maximum working pressure||bar||2||2||2|
|Recommended working pressure||bar||1.2-1.3||1.2-1.3||1.2-1.3|
|Power supply voltage||V/Hz/W||230/50/400||230/50/400||230/50/400|
|Capacity pellets hopper||kg||12||13||25|
|Recommended fuel||wood pellets, ø 6÷8 mm
/EN ISO 17225-2:2014/
|Incoming-air tube, diameter||mm||ø50||ø50||ø50|
|Tube exhaust gas -Chimney connection||mm||ø80||ø80||ø80|
|Outlet water jacket||Niplle 1”||Niplle 1”||Niplle 1”|
|Water jacket entrance||Niplle 1”||Niplle 1”||Niplle 1”|
|Exhaust gas temperature||0С||<180||<180||<180|
|Average fuel consumption per hour||kg/h||0.8||1.1||1.5|
|Burn time of full pellet hopper at max.power||h||4.5||4||5|
|CO content calculated to 13% O2 i
n the flue gas at nominal heat output